Watch Lee Kaiser speak about trending technology in clean agent fire suppression. In the video excerpt below, you can watch as he outlines the application of in cabinet fire suppression technology.
Want Access to the Full Video?
There is much more information available in the full video than we will be releasing in our blog series. Don't miss out! If you'd like to watch the entire Trending Technology Clean Agent Systems portion of the seminar, click here to receive the full video.
We see these small systems being installed in energy uses, specifically wind turbines and small emergency generators. When wind turbines catch on fire they can be quite spectacular--and sometimes you can see...go out and look at YouTube videos of them--but the small systems can be used up here and in the cells where all the generator equipment is, as well as down at the base of the unit where all the control equipment is. And we also use these systems in cabinets. And so I've got a video of a little fire test with a fire trace system installed in the cabinet, and they're going to light a fire at the bottom and in the middle, and you'll watch the system extinguish both fires.
Now, what's important to note about that particular test is that you mentioned they should be in an enclosed area. They actually did that test with the door open and it still extinguished the fires. Per NFP 2001, the Clean Agent Code, that door should be held shut and that normal condition would be for that door to be shut, but we can see that even in this case, they got lucky and still extinguished it with the door open. And so some places where I've basically got boxes that I want to protect, I think about mission critical and IT looking at server cabinets, even modular data centers that you don't have from-the-factory, fire-protection systems installed, power distribution (another great place), any time we have electrical gear, switch gear, UPS cabinets, electrical cabinets, and motor control centers.
This picture here that pops up is of a motor control center with a fire trace system installed on it that had a fire. Here, this larger orange tube is the fire trace tube and down here where the wires are black is actually where the fire started and impinged upon the tube, and that's where it burst and put out the fire.
This is part 9 of the Trending Technology Clean Agent Systems series. Watch the other parts at the links below:
- Part 1: What Are Clean Agent Fire Suppression Systems?
- Part 2: Are Fire Suppression Clean Agents Safe for People?
- Part 3: Common Applications of Clean Agent Systems
- Part 4: Types of Clean Agent Gases
- Part 5: How Do Clean Agent Systems Work?
- Part 6: New Technology in High Pressure Fire Suppression Systems
- Part 7: Trending Options for Localized Fire Suppression
- Part 8: Localized Fire Suppression Case Study CNC Machine
- Part 10: Advantages & Disadvantages of Rack Mounted Fire Suppression in Data Centers
You can also watch our previous series on Dialer and Communicator Technology Changes at the links below: